Top hat rail patch panel for one RJ45 port, SC-RJ or E-2000™ Compact, polycarbonate, integral shield termination, complying with standard DIN EN 50022 for 35-mm top hat rails and standard DIN 43880 for built-in equipment for electrical installations, designed to accommodate the R&M security and the R&M environment system. The security system's 3-level protection concept comprises optionally visual coding, combined mechanical-visual coding or the locking of individual ports.
And one shielded RJ45 connection module of Cat6, for the setting up of transmission channels of class E and class EA (and Cat6/Cat6A) with up to 4 plugged connections, and class F on 2 pairs, complies with Cat6 requirements of the standards ISO/IEC 11801 ed. 2.2, June 2011, EN 50173-1, May 2011 (DIN EN 50173-1) as well as TIA 568-C, de-embedded tested in acc. with IEC 60603-7-5, interoperable and backwards compatible with Cat5e and Cat5.
Suitable for 10GBASE-T applications in acc. with IEEE 802.3™ Section Four up to 500 MHz and 100 m.
Tested on the basis of the R&M production control including 100% routine test plus permanent quality assurance through the "GHMT PREMIUM Verification Program" including certificate and test report acc. to DIN EN ISO/IEC 17025, in German language.
Compatible with RJ standard plugs (RJ11, RJ12, RJ45), PCB-free and tool-free Easy-Lock connection of installation cables AWG 24 – 22 (0.5 mm – 0.65 mm) and flexible cables AWG 26/7 – AWG 22/7. Parallel pair termination without crossover in acc. with TIA 568-A/B, gold-plated bronze contacts for >1000 mating cycles, IDC contacts with single-wire strain relief and >20 insertion cycles, contact resistance <50 mOhm, dielectric strength >1000 Veff. Shield contacting by patented shield lance with integral cable strain relief, shield material tin-coated bronze, ground contacting through 2 contact fingers for flat connectors 4.8 x 0.5 mm.<BR/>Material: halogen-free and heavy-metal free in acc. with EU directives RoHS 2.
Connection module Cat6, shielded, with EMC cover, dust cover, mounting plate, cable tie and installation instructions.